:  Jakarta Pusat
:  17 hours ago
Sumber Berkat Abadi, We Are Specialist For Auto Synchronous Generators, Battery Chargers, AVR, Solenoid, Starter Motor, COS & Spare Parts Generators :
- Modul Synchronous, Load Sharing & Speed Control = WOODWARD, Deepsea DSE, Smart Gen. Comap, Datakom
- Battery Charger = BAE, SEG, CSS, Firetroll, BAC, DSE, SMPS
- COS = Kyoritsu, Takada & Socomec.
- AVR = Stamford, Basler, OEM, & Leroy Somer
- Starter Motor = Bosch, Hitachi, Mahle, etc
- Solenoid = Woodward, OEM,
DIJAMIN ANDA PUAS 100%
BERGARANSI selama 3 BULAN
Jika Rusak / Tidak Berfungsi, maka Modul kami Ganti Baru
(Bukan di Repair / diperbaiki, Namun GANTI MODUL BARU)
Garansi Tidak Berlaku, jika :
- Salah Pemasangan
- Komponen Terbakar
- Induksi Petir
Under- and over-frequency supervision of single or three-phase systems.
The unit BF1 is equipped with an independent over (f>) and under-frequency supervision (f<) with separate adjustable pickup values and trip delays.
The measured frequency is continuously compared with the set reference values.
For frequency supervision the cycle duration is evaluated and so measuring is virtually independent on harmonics.
To avoid tripping during normal operation due to interference voltages, a fixed measuring repetition is used.
rate voltage Un: 110V, 230V, 400 V AC
frequency range at
50 Hz rated frequency : 46 - 54 Hz
60 Hz rater frequency : 55,2 - 64,8 Hz
hysteresis : 0,5% of nominal frequency
power consumption : 3,7 VA
thermal load carrying capacity : continuously 1,3 x Un
returning time : 250 ms
minimum operating time : 250 ms
max. breaking capacity ohm ic : 250 V AC/120 W DC
inductive : 500 V AC/75 W DC
rated current : 5 A
making current : 20 A
regulations : VDE 0435 part 303
at storage and operation : - 25 0C bis + 70 0C
shock : class 1 acc. to DIN IEC 255-21-2
vibration : class 1 acc. to DIN IEC 255-21-1
degree of protection : IP 40 at closed front cover
weight : approx. 0,5 kg
mounting position : any
The unit BF1 is designed to be fastened onto a DIN rail acc. to DIN EN 50022 same as all units of the BASIC LINE.
The front plate of the unit is protected with a salable transparent cover (IP40)
Please remove the transparent cover with a screw driver to adjust the relay.
LED f< is used to indicate operation without fault with steady light. LEDs f> and f< indicate pickup of the relay by flashing.
at under-frequency tripping LED f< extinguishes. LED f> indicates tripping at over-frequency (steady light).